Mixed-mode ventilative cooling opportunity for an existing shopping mall retrofit
De Carli M
MetadataShow full item record
SubjectMixed-mode strategy; Electricity consumption reduction; Shopping mall; Common area retrofit; Ventilative cooling
Shopping centres currently design has included a small portion of automated windows sized for smoke ventilation. Their presence is mandatory for fire regulation and they are usually operated just in case of fire. Nevertheless, these buildings can potentially take advantage of those openable windows to exploit the potential of natural ventilation to guarantee the minimum air change rate required by IAQ standards and for ventilative cooling purpose reducing cooling and electrical consumption. The work presented in this paper investigate the retrofit performance potential of a mixed-mode ventilative cooling strategy tailor-made for an existing shopping centre. At the present, natural ventilation in the case study common areas is provided just on the basis of the energy manager judgment, without taking into account a robust control strategy based on indoor-outdoor climatic condition, thermal comfort and building use. A building model was created within TRNSYS environment and calibrated based on the real monthly electrical energy consumption. Then, with the support of the TRNFLOW plug-in, that couple thermal and airflow simulations, we were able to simulate and test the effectiveness of the tailor-made mixed-mode strategy. The simulation results show that windows opening can be operated starting from March to November. Running common areas with mixed-mode strategy over a year can allow to save 265 MWh which means cutting the electrical consumption by 23%.The initial costs for control strategies implementation can be paid in the first year of operation. The main contribution of this work is to demonstrate the feasibility of a mixed-mode ventilative cooling solution for an existing shopping mall common area retrofit highlighting how the exploitation of existing automated windows makes the solution cost-effective.
Showing items related by title, author, creator and subject.
Belleri A; Avantaggiato M (2016)Nearly all retail buildings use ventilation and cooling systems to ensure adequate air exchange, primarily for hygienic reasons, and indoor comfort temperatures. The ventilation systems that provide for a continuous inflow ...
Belleri A; Avantaggiato M; Lollini R (2017)Nearly all retail locations use ventilation and cooling systems to ensure adequate air exchange for health reasons and indoor comfort temperatures. These systems can run for over 2,000 hours per year and we expect that ...
Evaluation on the performances of a ventilated and non-ventilated cavity behind a BIPV: modelling and experimental monitoring Pinotti R; Maturi L; Avesani S; Babich F; Gasparella A (2018)Integrating electronic parts and batteries for stand-alone solutions in unitized curtain wall system is an innovative concept. This brings new challenges and problems that are investigated by this research. Since these ...